8-100 ASSEMBLE OIL LEVEL INDICATOR (Continued)
In following step 4., do not cover drain
hole with tape. Failure to comply could
cause accumulation of oil. This could
cause faulty oil level indication.
4. Install insulation tape (8) inside housing (3).
Use insulation tape (E42). Do not cover drain
hole (9). Center insulation tape between switch
mounting holes (10).
5. Install two wires(11 and 12) as follows:
a. Cut wires (11 and 12) to 1 1/2-inch length.
Use wire (E59).
b. Strip both ends of wires (11 and 12) to 1/4
c. Tin both ends of wires (11 and 12). Use sol-
d. Cut 1/2-inch piece of insulation sleeving (E24).
Slide sleeving (13) over wire (12).
GO TO NEXT PAGE