8-83 INSTALL NO. 4 AND 5 BEARING FILTER (Continued)
perform steps 1 thru 3. If reducer was
not removed, omit steps 1 thru 3.
1 Determine shims needed under reducer (1) as
Do not tighten reducer in following
step. Tightening of reducer may dam-
age internal oil tube.
a. Thread reducer (1) in adapter (2) until it is
In following step, fireshield must be
seated against adapter to obtain cor-
rect measurement. Failure to do so
will result in incorrect gap.
b. Seat fireshield section (3) against adapter (2)
and measure gap between fireshield section
and reducer (1).
GO TO NEXT PAGE