MARINE CORPS TM 6115-12/7
PREVENTIVE MAINTENANCE CHECKS AND SERVICES (PMCS)
3-3. GENERAL. TO
generator set is ready for operation at
it must be inspected system-
atically so that defects may be dis-
covered and corrected before they re-
sult in serious damage or failure.
necessary preventive maintenance checks
and services (PMCS) that are to be
performed by Operator/Crew personnel
are listed and described in table 3-2.
shall be noted for future correction.
immediately if a de-
ficiency is noted that could damage the
shortcomings shall be recorded on the
applicable form together with the cor-
rective actions taken. Air Force users
refer to the applicable in-
spection manuals and work card sets in
the TO 35C2-3 series for periodic re-
and table 3-2 for detailed
Marine Corps users shall
refer to current issue of TM 11275-15-1.
3-4. (A, N,
TENANCE CHECKS AND SERVICES.
3-2 provides a listing of PMCS that
shall be performed by the Operator/Crew
The item numbers are listed
consecutively and indicate the sequence
Preventive Maintenance Checks and Services (PMCS)
B - Before operation
D - During operation
A - After operation
Total M/H: 0.8
Items to be inspected
Inspection procedures ___
Visually inspect unit for
Check ground cable and
ensure that generator set is properly
Ensure that set is free of
tools and rags and that there is no
spilled fuel or lubricating oil.
Ensure MASTER SWITCH is in OFF position.
Ensure that panel lights and press-
to-test indicators operate properly.
Inspect meters and indicators for broken
glass and missing indicator lamps.