Figure 2-18. Operation to Deliver Compressed Air (TS 6115-590-12/2-18)
corrosion damage to direct support maintenance.
2-20. Operation in Snow
a. The power plant will operate satisfactorily during
snow conditions. However, precautions should be
taken to prevent accumulation of snow at the power
b. Observe procedures described for operation in
extreme cold (paragraph 2-15).
c. Erect suitable barriers to prevent air inlet and
exhaust openings from being clogged by driven
Barriers must not block the air flow during
operation. Install anti-icing hose to air intake
filter deicer manifold if temperatures approach
periodically to insure that no ice is forming on
the air filter.
d. Prevent snow from collecting around access
panels and door so as to prevent opening.
2-21. Operation in Mud
a. The power plant will operate satisfactorily in
mud provided sufficient support is provided the
skids from sinking to the point that mud blocks the