Figure 2-14. Operation to Deliver 400 Hz Electrical Power. (TS 6115-590-12/2-14)
(4) After power plant has cooled, carefully
unroll tarpaulin cover and cover the power plant.
Secure all tiedown straps.
2-12. Operation of Equipment
a. Operation to Deliver 60 Hz Electrical Power.
Refer to fig. 2-13 for operation of the 60 Hz
b. Operation to Deliver 400 Hz Electrical Power.
Refer to fig. 2-14 for operation of the 400 Hz
c. Operation to Deliver Cooled Air. Refer to fig.
2-15 for operation of the cooled air system.
Make up air doors (fig. 2-10) should be opened as
required during operation of the cooled air system
to permit intake of make up air to the system
Condenser air inlet panels and condenser air
outlet doors (fig. 2-10) must be open before
operating the cooled air system.