ASSEMBLE OIL LEVEL INDICATOR (Continued)
In following step 4, do not cover drain hole with tape. Failure to comply could cause accumulation of
oil. This could cause faulty oil level Indication.
4. Install teflon tape (8) inside housing (3). Use Pressure sensitive teflon tape (E46). Do not cover drain hole (9).
Center teflon tape between switch mounting holes (10).
5. Install two wires (11 and 12) as follows:
a. Cut wires (11 and 12) to 1-1/2-inch length. Use wire ((E65).
b. Strip both ends of wires (11 and 12) to 1/4-inch length.
c. Tin both ends of wires (11 and 12). Use solder (E54) and soldering iron.
d. Cut 1/2-inch piece of insulation sleeving (E28). Slide sleeving (13) over wire (12).
e. Solder wire (11) to bracket (14). Use solder (E54) and soldering iron.
GO TO NEXT PAGE