INSTALL FIRESHIELD SECTION (Continued)
2. Determine shims needed under reducer (5) as
Do not tighten reducer in following step.
Tightening of reducer may damage
internal oil tube
a. Thread reducer (5) in adapter (6) until it is seated.
In following step b, fireshield must be
seated against adapter to obtain correct
measurement. Failure to do so will result
in incorrect gap
b. Seat fireshield section (2) against adapter (6) and
measure gap between fireshield section and reducer
GO TO NEXT PAGE